# Remote sensor parameters

Complete information about Remote sensors type and connection.

Sensor name: name of the sensor connected to the SNMP adapter.

Type of sensor: temperature, humidity or digital I/O.

Name of the UPS: name of the UPS connected to the SNMP adapter with which the sensors have been associated.
Note: this combo box shows only the UPS for which the item “Remote Sensors” has been selected in the UPS configuration.

Sensor index: index of the sensors (from 1 to 6) connected to the SNMP adapter.

Temperature and humidity thresholds: maximum and minimum temperature and humidity threshold settings on the sensor. When these values are exceeded, the actions specified for the respective alarm in the Jobs tabs will be carried out.
Note: humidity thresholds are active only for humidity type sensors.

Digital input parameter: determines whether the digital I/O sensor has the input contact normally open (the alarm is triggered when the contact is closed) or normally closed (the alarm is triggered when the contact is opened).
Note: this section is active only for digital I/O type sensors.

Digital output parameter: determines whether the digital I/O sensor must close the output contact when a general alarm occurs on any of the sensors associated with the same SNMP adapter (switching for sensor alarm), and/or when an alarm occurs on the UPS connected to the same adapter (switching for UPS alarm).
Note: this section is active only for digital I/O type sensors.